Calder Services specialise in the fitting and servicing of oil storage tanks for central heating. Calder Services install and recommend market leaders Kingspan Titan oil tanks.
The Kingspan range of oil tanks is specifically designed and built to be the first choice for home-owners, contractors, developers and businesses. Our oil storage tanks are manufactured to the very highest of standards that far exceed all current regulations and safety standards.
Oil storage tanks should be inspected annually as part of your heating system’s regular service visit as like all your other heating products they have an expected working life (typically 10 – 15 years) and, if used beyond this time, the risk of a costly tank failure increases.
There are a number of guidelines and regulations applicable to the storage of heating oil it is quite possible you will be required to install a bunded oil tank or a fireproof oil tanks. If you would like an oil tank risk assessment or just some friendly advice about replacement oil storage tanks then Calder Services have friendly but professional OFTEC registered technicians who are ready, willing and able to help.
If however you would prefer to do a little bit of your own research first then take a look at the OFTEC home guide to Domestic Oil Storage here or check out their website at http://www.oftec.org/
This Home Guide applies to oil storage tanks up to 3500 litres capacity supplying oil to single family dwellings for heating and cooking purposes. For information on larger tanks, or non-domestic sites such as churches or village halls, please contact OFTEC’s technical team on 0845 65 85 080 (option 3) or email firstname.lastname@example.org. Depending on where you live, regulations may vary slightly. The information here is a general guide, and you should check with your nearest OFTEC registered technician which regulations affect you.
Modern oil storage tanks come in all shapes and sizes and can be made from plastic or steel. The size and type that your OFTEC registered technician recommends will depend on your individual requirements. It is recommended that the chosen tank is manufactured to OFTEC Standards (OFS T100 for plastic or OFS T200 for steel). A list of tank manufacturers can be found in the Equipment Directory on the OFTEC website at www.oftec.org
Your oil tank should be inspected annually as part of your heating system’s regular service visit. Oil tanks, like all heating products, have an expected working life (typically 10 – 15 years) and, if used beyond this time, the risk of a costly tank failure increases. The tank manufacturer or your servicing technician can advise you on when you should consider replacing your tank.
To minimise the risk of pollution from an oil spill, some installations must have secondary containment (a bund). This can be achieved by either choosing an integrally bunded tank or constructing a bund around a tank. The bund must be capable of holding at least 110% of the tank’s contents.
Your OFTEC registered technician will be able to advise whether you need a bunded tank using a standard risk assessment. Typically, installations near a river, well or any controlled water are likely to require bunding.
It is unlikely that a fire could be started by a domestic oil storage tank and its contents. However, tanks are required to comply with fire separation distances in order to adequately protect the stored fuel from a fire or heat source, that may originate nearby.
If it is impossible to comply with these requirements, then a fire protection barrier with at least 30 minutes fire rating should be provided. A minimum separation distance of 100mm is required between the tank and fire rated barrier unless a larger distance is specified by the tank manufacturer. In some situations, the oil storage tank can be sited inside a building such as a garage or outhouse. Installations of this type require the tank to be self contained within a 60 minute fire rated chamber. Your OFTEC registered technician can advise further on this type of installation.
The need to provide a suitable base and support for your oil tank is of paramount importance for reasons of both safety and environmental protection. The base should be:
If an oil storage tank is not adequately supported, the tank itself can be weakened leading to the eventual failure and escape of the stored fuel. During the life of an installation an oil storage tank base will need to provide continual structural support, even though ground conditions may alter from season to season and year to year.
Oil storage tank installations need to comply with regional Building Regulations. In England and Wales, OFTEC registered technicians can self certify their own work without involving Local Authority Building Control. But if you choose to use someone who isn’t registered with a ‘Competent Person’ scheme like OFTEC, then you will have to obtain a Building Control Notice and arrange for an inspection which can be costly and time consuming. Similar rules apply in Scotland where you may need to apply for a warrant. Your OFTEC registered technician can advise you on this.
OFTEC are the leading trade association for the Oil Heating and Cooking Industry.
Foxwood House, Dobbs Lane, Kesgrave, Ipswich IP5 2QQ Tel: 0845 65 85 080 Fax: 0845 65 85 181